API 653 Tank Repairs, Bradley Field ANG
USACE Omaha District
Project Delivery Method
KEAR Civil Corporation, as the prime contractor on this project, was contracted to perform API 653 repairs to Two above-ground storage tanks at Bradley Air National Guard in Bradley, CT. For the tanks at Facility 10418, KEAR Removed and Replaced the tank bottom chime extension with the annular ring, provided ringwall to tank bottom sealant, Repaired the containment dike, level alarms, tank stairs, manways, low suction line, thermal relief piping, water draw-off system, stilling wells, issue piping, receipt piping, center vent screens, tank grounding, supports, and repaired the spill containment walls. After all, work was complete the tanks were re-strapped, and a final API 653 inspection report was completed. KEAR managed all aspects of this project including preconstruction services, design, construction, and final acceptance.